The SSR is disconnected after the input is cut off
When the SSR should be disconnected, measure the input voltage. If the measured voltage is lower than the voltage that must be released, it indicates that the release voltage of the breaker is too low, and the relay should be replaced. If the measured voltage is higher than the must-release voltage of the SSR, it is The wiring in front of the SSR input is faulty and must be corrected.
Used in control cabinets, cabinets and other electrical control circuit,according to the scheduled time automatically switch on or off the circuit.
Built-in microcontrollers, 0.1s ~100h wide delay range, repeat accuracy <0.2%. Knob setting, LED indicator shows working status. Variety of optionalrated voltage. DIN rail mounting.
|Rated control supply voltage||DC12V、AC/DC 24V~240V 50/60Hz|
|Rated power consumption||1W|
|Delay range||0.1s~ 100h multi-range adjustment|
|Repeat power-on interval||≥200ms|
|Contact configuration capacity(A)||1C/O:16A ,2C/0:16A, 3C/O:8A,2C/O+ 1 instant C/O:8A+ 16A|
|Class of pollution||III|
|Contact capacity ,||Ue/le AC240V/1.5A. AC380V/0.95A|
|Contact capacity||1C/0 ,2C/0,3C/O,2C/0+1 instant C/O|